IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. 5. Voltages limited by arresters. Arrester power frequency witstand voltage. Resulting . An allowance of at least 5% (IEC ) is recommended. With this.
|Published (Last):||22 February 2013|
|PDF File Size:||11.66 Mb|
|ePub File Size:||15.18 Mb|
|Price:||Free* [*Free Regsitration Required]|
Selection and application recommendations Article no: What is a standard? Read more about SIS Subscriptions.
Subscribe on standards – Read more. Your shopping cart is empty.
The standard is now in your shopping cart. Annexes H and I present comparisons and calculations between old line discharge classification and new charge classification. Iecc edition includes the following significant technical changes with respect to the previous edition regarding the new surge arrester classification introduced in IEC Contact us svenska Login.
Surge protective devices connected to telecommunications and signalling networks – Performance requirements and testing methods. Do you need a ie copy? Selection and application recommendations Status: Sustainable Development Goals and standardisation, how do they connect?
IEC | IEC Webstore
Our prices are in Swiss francs CHF. Shopping cart Close cart 0, foreach: Fuses and other overcurrent protection devices Substations, surge arresters. It is likely, however, that for some systems, or in some countries, the requirements on system reliability and design are sufficiently uniform, so that the recommendations of the present standard may lead to the definition of narrow ranges of arresters.
Surge arrester residual voltage is a major parameter to which most users have 6009 a lot of attention to when selecting the type and rating. Selection and application recommendations.
This third edition cancels and replaces the second edition published in This edition constitutes a technical revision.
The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of characteristics resulting from prior practice may be continued. The Redline version is not an official document, it is available in English only and provides you with a quick and easy way to oec all the changes between the official IEC Standard and its previous edition.
Please note that the selected standard is invalid.
TC 37 – Surge arresters rss. The following test report forms are related: We accept all major credit cards American Express, Mastercard and 60099PayPal and bank transfers as form of payment.
It applies to 60099 metal-oxide surge arresters as defined in IECto surge arresters containing both series and parallel gapped structure — rated 52 kV and less as defined in IEC and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines EGLA as defined in IEC Message to your colleague.
Related publications IEC Preview Abstract IEC Typical maximum residual voltages are given in Annex F. In Annex J, some aspects regarding the old type of SiC gapped arresters are discussed.
IEC System of Conformity Assessment Schemes
Surge arresters – Part 5: Report error on page. Valid Buy this standard. SS Uec type surge arresters – Terminology. Subscribe on standards with our subscription service.